System type: ICS
ICS collector has no problem.
The freeze prevention valve is starting to leak. I told the resident to get it replaced. Said he would. Provided local contact.
Client is very happy with his system. Has three daughters and appreciates the solar system.
Insulation tape is deteriorating thereby allowing insulation to split open and expose copper piping at some locations.